The PV combiner box should be installed close to the PV modules.
The fuses should be able to interrupt the low-fault currents resulting from the failure of the solar cells while they also cope with high fault currents that may result from failure of an inverter. Rated current of the fuse is coordinated with the short-circuit current of the PV module. Two fuses for each string, installed in off-load fuse disconnectors with neon lamp indicator for blown fuse indication is provided.
Type 1/2 lightning/surge arrester or Type 2 surge is installed. If the building is equipped with external lightning protection, Type 1/2 lightning/surge arrester shall be used. For buildings without external lightning protection, Type 2 surge arrester can be used.